Alfa Laval AC Brazed Plate Heat Exchangers
Alfa Laval AC line of brazed plate heat exchangers provide efficient heat transfer with a small footprint. They are specifically developed to work in air conditioning, refrigeration, chillers and heat pump applications.
Brazed plate heat exchangers are widely used in refrigeration plants. They are normally used to transfer heat from the refrigerant – the primary fluid – and from water or brine as the secondary fluid.
Units in the Alfa Laval AC line of copper-brazed heat exchangers are mainly used as:
Evaporators for dry expansion and cooling water
Condensers for rejecting or recovering heat to water
Economizers for cooling liquid refrigerant and super-heating vapour refrigerant.
They can also be used as:
Sub-coolers to cool liquid refrigerants using well water
Intermediate heat exchangers in the absorption cycle, to preheat the diluted solution or to pre-cool the concentrated solution.
How it works
Brazed plate heat exchangers used for HVAC applications normally use a parallel flow to achieve the most efficient heat transfer. In a single-pass design, all the connections are located on one side of the heat exchanger, making installation very easy.
Alternate channel pattern
When used as an evaporator, the channels formed between the corrugated plates and corners are arranged so the two media flow through alternate channels, always in opposite directions (counter-current flow). The two-phase refrigerant (vapour + liquid) enters at the bottom left of the unit. The vapour quality depends on operating conditions in the refrigeration plant.
Evaporation of the liquid phase takes place inside the channels. Some degree of superheating is always required – hence the process being called “dry expansion”. The dark blue and light blue arrows show the location of the refrigerant connections. The water (brine) to be cooled flows counter-currently in the opposite channel; the dark and light red arrows show where the water (brine) connections are.
AC line as condenser
When used as a condenser, the main components are still the same as for the evaporator. The refrigerant enters at the top left as a hot gas and starts to condense on the surface of the channels. Once fully condensed, it is then subcooled slightly, in a process called “free condensation”. The dark and light blue arrows show the location of the brine connections. The refrigerant flows counter-currently in the opposite channel and is cooled. The dark and light red arrows show where the refrigerant connections are.
AC112 / ACH112
AC220EQ / ACH220EQ / ACP220EQ
AC230DQ / ACH230DQ
AC230EQ / ACH230EQ
AC232DQ / ACH232DQ
Keeping you processing
For more information about our products and services please get in touch!
Internal Sales Manager
Call: 01777 712101